The objective of this App Note is to show how to design a filter for gridconnected inverters that are widely used in solar and wind generation plants. Namely, various topologies, and strategies to optimize the size, stability and the efficiency of the system will be covered.
Nowadays, environmental concerns are pushing society towards renewable and more efficient energy sources. Utilization of the aforementioned sources is made possible by using switching power conversion devices. However, in order to ensure a good quality of the grid voltage, it is essential to introduce a low-pass filter after the inverting stage.
• First order filter with attenuation 20 dB/decade
• Suitable for converter with high switching frequency
• Decreases dynamics of the whole system
• Second order filter with attenuation 40 dB/decade
• The resonant frequency of the filter is dependent on the grid
• Attenuation of 60 dB/decade for frequencies above resonant frequency
• Better decoupling between the filter and the grid impedance
DESIGN PROCEDURE FOR LCL FILTERS
LCL topology is selected for grid connected inverter filters due to its advantages described in topology selection section.
Filter capacitance should be designed for maximum grid power factor variation of 5%.(x=0.05)
Inverter side inductor is designed to limit the ripple current to a certain amount, normally 10% of the rated current. (k=0.1)
Where Sn is the rated apparent power, and Vn is the line to line RMS voltage.
Grid side inductor is designed to limit the dominant harmonic current amplitude to the specified limit.
• IDH is amplitude of the dominant harmonic
• IlimDH is desired amp. the dominant harmonic
FFT ANALYSIS AND RESULTS
These figures show how changing the value of k, it is possible to tailor the filter for specific needs. Figure on the left demonstrates how values of grid side and inverter side inductances change with k from 0.1 to 0.5, with the minimum total inductance appearing at k=0.34.
However, the figure on the right shows that total harmonic distortion on the inverter side increases with the increasing k, as expected.
So, using this method, the design of an LCL filter can be optimized based on the desired size relation between inductors, and allowable THD and power losses.
In high power, grid-connected applications, the size, efficiency, and cost of a filter, as well as the total harmonic distortion, can be of foremost importance. After learning from the described design procedure and its implementation, Frenetic's artificial intelligence can obtain the most optimal filter design along with the advanced magnetic design of inductors for your application.